Friday from the field:
1. Customer’s system was backing in home after days of gurgling and toilets draining slow, even though she had it pumped within 2 years.
2. Tank condition was fine. I noticed when opening the lid that the inlet Tee and line was clogged with grease slowing flow and eventually leading to a back up.
3. Visually saw grease all in the inlet baffle Tee and no water draining from home.
4. Cleared Tee of grease, snaked line to make sure all grease was free. Had customer run all water in home to free any loose grease or objects that could still be in line.
Was able to save her a pump charge and only a service charge while also freeing up the clog!
Give us a call for all your septic tank needs!!
~The Doo Doo Guru
BACKHOE WORK • SEWER PUMPS • SEPTIC TANKS • GREASE TRAPS • DRAIN FIELDS • TANK REPAIRS • JETTER SERVICE • LINE LOCATOR • HOME SEPTIC INSPECTION LETTERS