This week’s “on the job”
Austin shared this about one of his jobs this week:
A customer called because the alarm was going off on the pump tank. She had assumed the pump tank was the only tank. We were able to inform her that she actually had 2 tanks and this was the first cleaning since the home was built.
The older pump had gone out so she needed a servicing on the primary tank and also a pump replacement in the secondary tank.
We were able to access sludge that had been carried to the secondary tank so that meant the primary tank had to be in rough condition if sludge was pushing through the baffle and filtration process.
So, we pumped the septic and pump tank, removed the pump and float, replaced both with a newer updated model and float switch. Her system is now working properly.
Don’t forget to call us for all your septic and grease needs!
BACKHOE WORK • SEWER PUMPS • SEPTIC TANKS • GREASE TRAPS • DRAIN FIELDS • TANK REPAIRS • JETTER SERVICE • LINE LOCATOR • HOME SEPTIC INSPECTION LETTERS